BVY 14-036, Response to Request for Additional Information on Technical Specifications Proposed Change No. 306, Eliminate Certain ESF Requirements During Movement of Irradiated Fuel - Supplement 1
NG-94-2629, Application for Amend to License DPR-49,proposing Changes to Ts,By Increasing Allowable Main Steam Isolation Valve Leakage & Deleting TS Requirements Applicable to MSIV LCS
NG-94-0794, Request for TS (RTS-246A) Rev to RTS-246 to License DPR-49, Revising TS Section 3.7, Containment Sys
05000259/LER-1987-014-01, :on 870708,control Room Emergency Ventilation Sys Measured Flow Rates in Excess of Design Basis Flow Rate. Caused by Throttle Dampers Not Set to Deliver Flow on Optimum Filtration.Procedure to Be Revised
05000259/LER-1987-014, :on 870708,engineers Measured Flow Rates in Excess of Design Basis Flow Rate.Throttle Dampers on Two Control Room Emergency Ventilation Units Unset Since Sys Installation.Procedures Revised
05000277/LER-1992-016-01, :on 920911,discovered That Containment Venting & Outgoing Activities Had Been Started While SBGTS Awas Removed from Svc & Inoperable.Caused by Personnel Error. Containment de-inerting Terminated
05000280/LER-1982-086-03, /03L-0:on 820827,radiation Monitor RM-LW-10F Indicated 9.0E4 CPM W/O Annunciation of Alarm.Caused by Defective Push Button & Setpoint Drift.Push Button Replaced & Monitor Recalibr
05000280/LER-1982-075-03, /03L-0:on 820626,setpoint for CC Rad Monitor RM-CC-105 Discovered Greater than Twice Background.Caused by Decreasing Activity in Computer Cooling Sys.Setpoint Readjusted W/New Background Activity Levels
05000331/LER-1982-012-03, /03L-0:on 820208,during Surveillance Testing,Msiv Leakage Control Sys Bypass Valve MOV-8403C Failed to Close. Caused by Failed Auxiliary Switch on Motor Starter Contractor Coil Mfg by Allis Chalmers.Switch Replaced
05000331/LER-1981-037-01, /01T-0:on 811017,during Valve Lineup Check,Main Steam Line Leakage Control Sys D Manual Valve V-84-16 Was Found Closed.Caused by Valving Error Due to Poor Lighting & Accessibility & Lack of Valve Labels.Lineup Performed
05000280/LER-1981-042-03, /03L-0:on 810902,high Alarm Setpoint for Component Cooling Radiation Monitor RM-CC-105 Was Exceeded W/O Surge Tank Vent Closing or Annunciator Alarming.Caused by Failed Log Ratemeter Card.Card Replaced & Instrument Recalibr
05000280/LER-1981-062-03, /03L-0:on 811017,radiation Monitor RI-CC-105 Failed to Give Indication.Caused by Broken Wire Located on Detector Probe.Wire Reconnected
05000298/LER-1979-013-03, /03L-0 on 790508:correct Drywell to Suppression Chamber Reading Not Established.Caused by Leaking Inlet Purge Valve.Valve Repaired & Leak Tested
05000280/LER-1979-015-03, /03L-0 on 790422:liquid Waste Disposal Radiation Monitor Failed to Give High Alarm & Trip Release Valve. Caused by Procedural Inadequacy.Procedures Modified
05000259/LER-1987-006-01, :on 870302,discovered That Routine Flow Rate Surveillance on Control Room Emergency Ventilation Train B Performed Incorrectly on 870301.Caused by Personnel Error. Correct Zeroing Procedure Clarified
05000259/LER-1987-006, :on 870302,discovered That Routine Flow Rate Surveillance on Control Room Emergency Ventilation Train B Performed Incorrectly Night Before.Caused by Personnel Error.Flow Measured & Correctly Set