NMP1L3070, License Amendment Request - Reactivity Anomalies Surveillance
RA-17-072, License Amendment Request - Proposed Defueled Technical Specifications and Revised License Conditions for Permanently Defueled Condition
BVY 13-053, Revision of Technical Specifications Bases Pages
BVY 13-022, Revision of Technical Specification Bases Pages
BVY 12-085, Technical Specifications Proposed Change No. 302 Inoperable Control Rods
BVY 12-030, Response to Request for Additional Information on Technical Specifications Proposed Change No. 298
BVY 12-006, Technical Specifications Proposed Change No. 298, Rod Worth Minimizer Bypass Allowance
BVY 09-068, Technical Specifications Proposed Change No. 288 Scram Discharge Volume Vent and Drain Valves
BVY 09-014, Submittal of Revised Technical Specification Bases Pages
BVY 08-047, Technical Specification Proposed Change No. 276, Response to Request for Additional Information
05000280/LER-1978-030-03, /03L-0 on 781009:w/unit at Rated Pwr,Charging Pump Component Cooling Water Pump Btripped.Pump Tripped on Overcurrent.Caused by Corrosion Damage to Motor Bearings. Pump & Motor Rebuilt & Reinstalled
BVY 05-032, Vermont Nuclear Power Station - Response to Request for Additional Information Regarding Intermediate Range Monitor Surveillance Test Frequencies
05000280/LER-2078-009-03, L Re Snubber Body in Contact with Structure; LER 1978-009-03L Re Trip of Boric Acid Transfer Pump; & LER 1978-010-03L Re Failure of Pressurizer Channel
NL-02-001, License Amendment Request - Detection of Technical Specifications for Reactor Vessel Material Surveillance Program
B17621, Application for Amend to License DPR-21,reflecting Permanently Defueled Condition of Unit 1,Tech Specs Administrative Controls Section as Allowed by Guidance Contained in NRC Administrative Ltr 95-06
NLS9100187, Application for Amend to License DPR-46,consisting of Proposed Change 90 Re Extended Load Line Limit & ARTS Improvement Program.Rev 1 to Rept NEDC-31892P Encl.Rept Withheld (Ref 10CFR2.790)
BVY 08-007, Technical Specification Proposed Change No. 276 Revision to TS Sections 3.3/4.3 for Control Rod System
05000286/LER-1986-009-01, :on 860902,control Room Switches for Two Containment Spray Pumps & Two Recirculation Sump Pumps Found in trip-pullout Position.Caused by Lack of Communication. Prewarmup Checkoff List & Procedures Revised
05000278/LER-1986-009-02, :on 860318,manual Scram Occurred.Caused by Series of Personnel Errors Involving Failure to Withdraw Correct Control Rod & Verify Proper Position of Control Rod. Personnel Counseled & Procedures Revised
05000280/LER-1976-012-03, /03L:on 760909,low Pressure Alarm Occurred on Safety Injection Accumulator C.Caused by HCV 1936 Partially Open & Body to Bonnet Leaks on HCV-1898 & 1549.Repairs Made on HCV 1936,1898 & 1549
05000281/LER-1976-012-03, /03L:on 760813,routine Sample of Safety Injection Accumulator C Indicated 1,893 Ppm Boron.Caused by Leaking Check Valves 2-SI-147 & 2-SI-145.During Refueling,Check Valves Will Be Inspected & Repaired
05000280/LER-1976-008-03, /03L:on 760702,safety Injection Accumulator B Indicated 1,928 Ppm Boron.Caused by Leaking Check Valves 1-SI-128 & 1-SI-130.Accumulator Recirculated in Raw Water Storage Tank to Increase Boron Concentration
05000280/LER-1977-006-03, /03L:on 770208,charging Pump Cooling Water Pump 1-CC-P-2A Tripped Due to Thermal Overload.Caused by Faulty Motor Bearings.Bearings Replaced & Minor Mechanical Defects Corrected
05000237/LER-1976-067-01, /01T-0:on 761203,GE Informed That Current Upper Limit of 10% Power for Required Rod Worth Minimizer Operation Not Sufficiently Conservative.Procedures Revised to Include New Upper Limit
05000237/LER-1983-067-03, /03L-0:on 830927,all LPRMs in Levels B & D Bypassed on Front Panel.Rod Block Monitor 8 Placed in Bypass.Caused by Blown Fuse in Power Supply.Fuse Replaced & Monitor 8 Returned to Svc
05000265/LER-1994-004-03, :on 940131,control Rod Coupling Integrity Neutron Instrumentation Response Test Untimely Completed. Caused by Failure to Prioritize & Track Completion of Qcos 300-4.Procedures Revised
05000259/LER-1982-069-03, /03L-0:on 820907,during Startup Testing,Rod Sequence Control Sys Found Inoperable.Caused by Failure of GE Sequence Generator Card Model 195B948GAA.Card Replaced & Testing Satisfactorily Completed
05000280/LER-1981-041-03, /03L-0:on 810820,PT-27D Revealed That Amp Readings for Heat Tracing Panel 9 Circuit 7A Were Below Acceptance Criteria.Caused by Inadvertent Cutting of Heat Tracing Tape During Cleanup Operations on Boric Acid Flat
JAFP-81-0457, Responds to NRC Re Violations Noted in IE Insp Rept 50-333/81-01.Corrective Actions:Required Review of Special Procedures for Abnormal & Emergency Operations Has Been Completed by Every Licensed Operator
05000306/LER-1980-035-03, /03L-0:on 801103,remote/local Control Switch on Containment Spray Pump 21 Found Not in Remote Position. Caused by Contractor Workman Bumping Switch.Switch Returned to Remote Position
05000333/LER-1981-030-03, /03L-0:on 810401,rod Sequence Control Sys Did Not Allow Normal Control Rod Movement.Caused by Failed Reed Switches in Control Rod Position Probes.Probes Replaced
05000306/LER-1980-022-03, /03L-0:on 800805,during Surveillance test,fan-coil Unit Dome Damper 23 Could Not Be Positioned Properly.Caused by Leaking Air Supply Line to Damper Actuator.Air Supply Line Replaced
05000321/LER-1980-018-03, /03L-0:on 800207,during Normal,Full Power Operation,Hydraulic Control Unit Accumulator 42-23 Received Low Pressure Alarm.Caused by Failure of Nitrogen Cartridge Valve from Wear Due to Constant Use
05000280/LER-2076-012, Re Routine Sample of C Safety Injection Accumulator Indication of 1893 Ppm Boron
05000281/LER-1992-001-03, :on 920130,charging Pump 2-CH-P-1A Declared Inoperable Due to Oil Leak & Ventilation Damper for Charging Pump B Cubicle Failed to Open.Caused by Mechanical Failure/Personnel Error.Pump Repaired
05000281/LER-1992-002-03, :on 920227,two Charging Pumps & One Charging Pump Svc Water Pump Removed from Svc Simultaneously.Caused by Congnitive Personnel Error.Senior Reactor Operator Disciplined & Pump Returned to Svc
05000280/LER-1993-012-01, :on 931015 & 1101,boron Concentration in Safety Injection Accumulator B Found to Be Below TS Limit Due to Cognitive Personnel Error.Accumulator Drain & Fill Procedures Will Be Changed
05000280/LER-1988-008-01, :on 880309,low Head Safety Injection Pump Inoperable Due to Failed Motor Leads Caused by Improper Splicing.Leads Repaired & Motor Replaced & Tested Satisfactorily
05000281/LER-1980-026-03, /03L-0:on 801005,w/reactor at 100% Power & Redundant Low Head Safety Injection Pump Out of Svc for Maint,Operator Failed to Retest Operable Pump 2-SI-P-1a within Specified Time.Caused by Operator Oversight
05000280/LER-1978-036-03, /03L-0 on 781107:failure of Heat Tracing Circuit 24D,Unit 1,due to Boric Acid Damage.Heat Tracing Tape Replaced
05000280/LER-1978-022-03, /03X-1 on 780726:Hydro Test Pump Failed to Build Up Pressure During Attempt to Fill Safety Injection Accumulators Due to Lifting of Its Relief Valve.Valve Replaced & Checked.Accumulator Refilled
05000237/LER-1976-074, For Dresden Unit 2 Regarding a Control Rod J-2 Withdrawal of One Notch and Reactivity Inserted by This Resulted in a Transient Power Increase
05000237/LER-1976-067, Regarding a General Electric Recommendation That the Upper Limit for RWM Operation Be Raised to 20% Reactor Power
BVY 05-094, Technical Specification Proposed Change No. 266, Revision to Control Rod Operability, Scram Time Testing and Control Rod Accumulators - Response to Request for Additional Information
05000278/LER-1986-023-02, :on 861104,reactor Protection Sys Initiated Full Reactor Scram During Main Turbine Shell Warming Procedure.Caused by Inadequate Design & Operator Error. Procedure Revised
05000281/LER-1983-039-03, /03L-0:on 830926,w/unit at Hot Shutdown,Auxiliary Oil Pump for Charging Pump 2-CH-P-1A Observed Not Running. Cause Undetermined.Starting Coil Removed & Inspected.No Problems Found.Pump Performs as Designed