PLA-3215, Forwards Summary Rept of Safety Evaluations Approved During 1988.Changes Include Backseating Control Box to Electrically Backset HV-202168 to Reduce Steam Leakage & Rerouting Condensate Supply Line to Main Condenser Keepfill
LR-N12-0160, Special Report - Safety/Relief Valve Position Indicators
LR-N10-0355, Hope Creek, HC.OP-AR.ZZ-0011(Q), Rev. 53, Overhead Annunciator Window Box C6
LR-N10-0218, Special Report - Filtration, Recirculation and Ventilation System Radiation Monitoring System
LR-N08-0164, Special Report - Safety Relief Valve (SRV) Acoustic Monitor
LR-N06-0097, Special Report, Accident Monitoring Instrumentation Action 81, Due to the Filtration Recirculation Ventilation System Radiation Monitor Being Inoperable for Greater than 72 Hours
U-601538, Responds to NRC Re Violations Noted in Insp Rept 50-461/89-26.Corrective Actions:Procedure 3001.01 Revised to Include Step in Prerequisite Section of Procedure to Place RHR in Standby Mode
LR-N05-0421, Special Report 354/05-006-00 for Hope Creek Generating Station Re South Plant Vent Radiation Monitoring System Being Inoperable for Greater than 72 Hours
NRC-88-0134, Special Rept:On 880527,div II Standby Gas Treatment Radiation Exhaust Accident Range Monitor Process Controller Discovered Switching Between Normal & Standby Modes & Declared Inoperable.Caused by Problem in 8K Board
NRC-98-0057, Application for Amend to License NPF-43,revising Requirements Associated W/Containment Oxygen & Hydrogen Monitors
NRC-98-0062, Application for Amend to License NPF-43,modifying Drywell Oxygen Monitoring Instrumentation Action Requirements to Be Consistent W/Those Contained in NUREG-1433,Rev 1, STS GE Plants,BWR/4
NRC-98-0071, Application for Amend to License NPF-43,proposing Align Shutdown Action Statements for Primary Containment Oxygen Monitoring Instrumentation in Three Specifications
U-601258, Special Rept:On 880803,accident Monitoring Instrumentation for HVAC Stack Declared Inoperable for More That 72 H.Caused by Underway Work to Perform Routine Channel Calibr.Plant Condition Rept Initiated
U-601118, Proposed Tech Specs Re Administrative Controls
AECM-88-0218, Submits Addl Info Re 880819 Application for Amend to License NPF-29,per NRC 881006 Request.Proposed Administrative Changes to Fire Protection Specs Per Generic Ltr 87-09, Included in Amend Request
AECM-85-0339, Special Rept 85-012:on 851002,limiting Condition for Operation Entered Under Tech Spec 3.3.7.5 When Turbine Bldg Ventilation Exhaust Accident Range Monitor Removed from Svc for Annual Calibr Surveillance
AECM-88-0181, Special Rept 88-005/0:on 880829,post-accident Monitoring Instrument for Standby Gas Treatment B Subsystem Exhaust Declared Inoperable & Left Inoperable for More than 72 H. Caused by Time Spent to Procure Replacement Part
U-602068, Ro:On 921107,ORIX-PR008 Was Declared Inoperable Due to Lo Fail Signal Received for Channel 3 Which Was Unable to Be Reset.Preplanned Alternate Method of Monitoring HVAC Stack Initiated
U-601952, Defers Completion of Corrective Action Described in Special Rept Re Temporary Inoperability of HVAC Stack High Range Radioactivity Monitor from 920228 to 920430
AECM-84-0229, Forwards Program Completion Rept Re Conclusion of Tech Spec Review Program.Rept Documents That Thorough & in-depth Engineering,Operations & Licensing Review of Tech Specs Conducted Per Programmatic Commitments
AECM-84-0027, Forwards Description of Implementation of Listed NUREG-0737 Items Per Generic Ltr 83-36.Current Tech Specs Consistent W/Requirements for NUREG-0737,Items II.B.1,II.B.3,II.F.1 & II.D.3.4
U-601893, Special Rept:On 911001,ORIX-PRO12 Declared Inoperable in Order to Perform Channel Calibr in Accordance W/Ts Surveillance Requirement 4.3.7.5.Calibr Initially Performed by day-shift C&I Crew,Then Backshift Crew
U-602085, Responds to NRC Re Violations Noted in Insp Rept 50-461/92-20.Corrective Actions:Search Performed on Plant Maintenance Planning Sys Equipment List to Identify Other Equipment in Use at Plant That Utilize Keyboard/Keypad
PY-CEI-NRR-0675, Special Rept NP-38-01:on 870617,post-accident Effluent Radiation Monitors Monthly Surveillance Channel Checks Dicovered Deficient in Meeting Tech Spec Requirements.Caused by Procedural deficiency.D19 Channel Checks Deleted
PY-CEI-NRR-0721, Special Rept NP-38-02:on 870901,accident Monitoring Instrumentation Inoperable on D19 Area Radiation Monitors. Caused by Degraded Insulation Resistance of Field Cable Sys. Action to Restore Channels to Operable Condition Continuing
PY-CEI-NRR-0469, Forwards List of Tech Spec Changes to Accompany Full Power Ol,Representing Minor Editorial Corrections,Clarifications & Enhancements.Justifications & Proposed marked-up Tech Spec Pages Also Encl
PY-CEI-NRR-0844, Special Rept NP-38-03:on 880407,turbine Bldg/Heater Bay Ventilation Exhaust post-accident Monitor (D19) Declared Inoperable.Caused by Electrical Failure on Interface/Relay Boards in Control Room Indication Unit
PY-CEI-NRR-1857, Special Rept:On 940825,offgas Ventilation Exhaust Post Accident RM Declared Inoperable & Exceeded 72 H Limit on 940828 When New Flow Control Circuit Card Would Not Calibr Properly.Original Circuit Card Reinstalled & Calibr
PY-CEI-NRR-1342, Special Rept:On 910319,turbine Bldg/Heater Bay Vent Post Accident Radiation Monitor Declared Inoperable to Facilitate Performance of Calibr Procedure.Work Order Revised to Replace Failed Regulator
PY-CEI-NRR-1756, Forwards Annual Rept of 10CFR50.59 Safety Evaluations for 1993
PY-CEI-NRR-1213, Special Rept:On 900807,radiological Effluent Monitoring Instrumentation Inoperable for 72 H.Caused by Default Setpoints.New Microcomputer Chips Installed in All post-accident Radiation Monitors
U-602155, Special Rept:On 930704,TS Time Limit Expired for SGTS Exhaust Stack High Range Radioactivity Monitor Declared Inoperable on 930701 Due to Low Sample Flow Reading. Suspected Degraded Pump Replaced.Followup Will Be Provided
PLA-1747, Ro:On 830628,review Revealed Reactor Bldg Station Particulate Iodine & Noble Gas Monitor Out Svc for More than 72 H During 820917-21 & 1201-14.Caused by Need to Work on Sample Probe & to Replace Pump
05000352/LER-1988-042, :on 881223,inoperability of Plant Sys Due to Unacceptable Physical Separation Between safety-related Cabling Determined.Caused by Personnel Error.Plant Procedure Will Incorporate Consolidated Open Items List.W/Undated Ltr
05000352/LER-1989-041, :on 890613,four Channels of Primary Containment post-LOCA Radiation Monitor Instrumentation Inoperable. Caused by Procedural Deficiency.Temporary Procedure Change Implemented to Affected Surveillance Tests
05000352/LER-1989-034, :on 890512,certain Excess Flow Check Valve Test Valves Would Not Remain Leak Tight During post-DBA Conditions.Caused by Inadequate Review of Sys Design Specs. All 19 Test Valves Removed
05000461/LER-1989-031, :on 890724,plant Entered Mode 2 Startup W/O Meeting Provisions of Tech Spec 3.0.4.Caused by Personnel Lack of Understanding of Tech Specs & Failure to Recognize Temp Recorder.Training on Tech Specs Increased
05000461/LER-1987-063, :on 871122,instrument Root Valve for Div 1 Reactor Vessel Pressure Transmitter Discovered Closed.Caused by Failure of Control & Instrumentation Technicians to Follow Procedures.Technicians Retrained
05000461/LER-1987-040, :on 870710,util Radiation Protection Personnel Discovered That Collection Media Missing from Particulate/ Iodine Sampler.Caused by Failure to Reinstall Media on 870703.Collection Media Reinstalled
05000354/LER-1987-004-03, :on 870610,north Plant Vent High Flow Sample Pump Inoperable for More than 72 H.Caused by Equipment Failure.Spare Parts for Equipment Problem on Order & Should Be Installed by 870627
05000354/LER-1987-003-03, :on 870420,primary Containment Hydrogen/Oxygen Concentration Analyzer & Monitor Declared Inoperable for More than 7 Days.Caused by Problems During Routine Surveillance.Util Granted 72 H Extension
05000387/LER-1986-034-01, :on 860925,discovered That Drywell Hydrogen Analyzer Channel a Inoperable Since 860626.Caused by Replacement Amplifier Board Having Soldered Wire Connector Installed in Circuitry.Connector Replaced
05000461/LER-1988-023, :on 880901,personnel Discovered Flush Valve for HVAC Monitor Grab Sample Pallet Open.Cause Attributed to Personnel Error.Procedures Upgraded to Require Performance of Complete Valve Lineup
05000354/LER-1998-005-03, :on 980810,discovered That Two Nitrogen Gas Supply Check Valves to B hydrogen-oxygen Analyzer Were Not Being Tested.Caused by Missed Ist.Ist Data Base Is Being Reviewed to Assure Completeness & Accuracy.With
05000373/LER-1996-010, :on 960829,violations of TS & Design Basis Occurred.Caused by Inadequate Standards for TS Clarification.Deleted Clarifications in Question on 960829 & Revised One Clarification
05000373/LER-1996-010-06, :on 960829,determined Conditions Outside of Design Basis.Caused by Inadequate Standards for TS Clarifications.Implemented Development of TS Clarifications & Evaluates TS Interpretations
05000354/LER-1992-012-02, :on 921017,RM Skid Declared Inoperable Due to Low Sample Flow Indication on Particulate,Iodine & Noble Gas Monitor Portion of Skid.Caused by Design Deficiency.Design Review of RMS Skid Will Be Performed
05000461/LER-1992-011, :on 921123,lack of Procedure for Software Changes to Hydrogen & Oxygen Analyzers Results in One of Two Analyzers Being Inoperable During Plant Mode Change.Caused by Lack of Work Document.Procedure Revised
05000354/LER-1991-020-01, :on 911207,personnel Received Indication of HPCI Isolation During Steam Line Warmup Following HPCI Outage.Caused by Improper Wiring of Temp Detector.Wiring Corrected & Delta-T Circuits Inspected
05000373/LER-1983-130-03, /03L-0:on 831021,stack wide-range Gas Monitor Alarm Received.Caused by Checksource Not Remaining Long Enough at Detector Window for Detector to respond.Mid-range Detector Manually Source Checked
05000416/LER-1983-160-03, /03L-0:on 831010,containment Hydrogen Monitor Declared Inoperable When Hydrogen Analyzer Cell Failure Light Alarmed & Would Not Clear.Caused by Analyzer Conductivity Cell Failure.Cell Replaced
05000416/LER-1983-164-03, /03L-0:on 831016,channel B Containment Hydrogen Monitor Declared Inoperable & Limiting Condition for Operation Entered When Hydrogen Analyzer Failed Monthly Calibr.Caused by Cell Failure.Cell Replaced
05000373/LER-1983-063-03, /03L-0:on 830613,w/Div II post-LOCA Hydrogen Monitor Out of Svc,Div I Hydrogen Recorder Read 1% & Declared Inoperable.Caused by Out of Calibr Hydrogen Analyzer Cell.Div I Monitor Recalibr
05000387/LER-1983-048-03, /03L-0:on 830315,operator Found Bottle Valve for Reagent Gas for Containment Hydrogen Analyzer B Closed. Probably Caused by Unidentified Person Shutting Valve. Operators Round Sheets Revised
05000387/LER-1983-090-03, /03L-0:on 830606,containment Atmosphere Hydrogen Dioxide Analyzer Placed in Svc from Standby Condition & Exhibited Erroneous Readings.Analyzers Declared Inoperable. Caused by Calibr Gas in Lines.Lines Purged
05000373/LER-1982-139-03, /03L-0:on 821030,Div 11 Oxygen Channel Was Reading Erratically.Caused by Moisture Buildup in Oxygen Sample Flowmeter.Moisture Removed & Instrumentation Recalibr
05000373/LER-1982-148-03, /03L-0:on 821112,Div II post-LOCA Oxygen Channel Indication Drifted Down to 4%.Caused by Instrument Drift, Resulting in False Indication.Adjustments Made to Sample Flows & Calibr Performed
05000387/LER-1983-022-03, /03L-0:on 830203,reagent Gas Bottle (Oxygen) for Hydrogen Analyzer Found Exhausted During Startup Test Program.Caused by Periodic Gas Bottle Pressure Check Omission & Inadequate Storeroom Min Inventory
05000353/LER-1990-018-02, :on 901030,north Stack Wide Range Monitor Exceeded 7-day Limit for Inoperability of Tech Spec 3.3.7.5
05000341/LER-1993-008, :on 930518,discovered That Recorder T50-R802A Could Not Be Considered Operable Per TS 3.3.7.5.Caused by Personnel Error.Lessons Learned Will Be Incorporated Into Training Programs & Plant Procedures
05000461/LER-1993-001-01, :on 930226,requirements of TS 3.3.7.5 Were Not Met Due to Vendor Failure to Design Flywheel & Unexplained Capped Constant Bleed Drain on Air Tank Resulting in High Compressor Current.Labels Installed.W/Undated Ltr
05000352/LER-1991-004, :on 910123,determined That TS Section 3.3.7.5 Surveillance Requirements Not Satisfied for Fuel Zone Level & Neutron Flux Instrumentation.Caused by Misinterpretation of Ts.Calibr Procedures Revised
05000373/LER-1982-167-03, /03L-0:on 821201,drywell Oxygen Monitoring Sys Failure Alarm Sounded in Control Room.Caused by Low Calibr Gas Bottle Pressure,Faulty Analyzing Cell & Defective Flow Regulator.Calibr Gas Bottle & Faulty Parts Replaced
PLA-4791, Responds to NRC Re Violations Noted in Insp Repts 50-387/97-80 & 50-388/97-80.Corrective Actions:Tsis 1/2-94-007 Were Deleted on 971002.PP&L Will Submit Change to Improved TSs to Delete Ref to Svc Platform Hoist Interlock
GO2-96-221, Special Rept:On 961023,intermediate & High Range Stack Monitors PRM-RE-1B & PRM-RE-1C Declared Inoperable.Caused by Monitor Output Had Upward Trend Due to Electronic Noise Interference.Work Request Generated
05000397/LER-1995-003, :on 940817,CR Indication Lost for PASS Inboard Ci Valve & Cycling for Restoration Erratic & Showed Continuous Closed Indication.Caused by Unclear TS Requirement.Ts Bases Will Be Revised
GO2-95-070, Responds to Violations Noted in Insp Rept 50-397/94-33. Corrective Actions:Redundant Outboard Containment Isolation Valve Deactivated Isolating Associated Sample Line
GO2-95-053, Special Rept:On 950305,reactor Bldg Effluent Monitoring Sys Was Inoperable for 72 Hrs.Caused by Failure of Stack Monitor Detector.Stack Monitor Returned to Svc on 950314
GO2-93-207, Informs That on 930726,control Room Received Main Steam Leakage Control Board W Trouble Alarm (S2-2.2) Due to Power Lost to Power Panel E-PP-7BC.Blown Fuses in Regulating Transformer That Feeds E-PP-7BC Replaced
GO2-92-046, Application for Amend to License NPF-21 TS 3/4.4.2 & 3/4/3/7/5 Recognizing Redundancy in SRV Position Indication. Direct Reading SRV Stem Position Indicator to Be Installed in Outage in Addition to Accoustic Monitoring Indication
GO2-90-038, Application for Amend to License NPF-21,revising Tech Spec 3.4.2, Safety Relief Valves & Tables 3.3.7.5-1 & 4.3.7.5-1, Accident Monitoring Instrumentation, to Allow Monitor on Safety Valves to Be Inoperable Until Shutdown
GO2-90-035, Forwards Supplementary Info Re 900214 Application for Amend to License NPF-21,revising Tech Spec 3.3.7.5 to Address Failed Safety/Relief Valve Position Indicators
GO2-92-032, Responds to Licensee Ltr Re Performance of Acoustic Monitors Used on Facility for Safety Relief Valve Position Indication
GO2-93-281, Application for Amend to License NPF-21,adding Footnote to TS Table 4.3.7.5-1, Accident Monitoring Instrumentation Srs, Exempting Channel Calibr of Safety/Relief Valve Position Indicators from Spec 4.0.4 for 24 H
GO2-94-247, Application for Amend to License NPF-21,revising TSs to Relocate Safety/Relief Valve Position Indication Instrumentation Requirements
GO2-96-179, Submits Response to Violations Noted in Insp Rept 50-397/96-15.Corrective Actions:Individuals Involved in 1993 Mod & Startup Testing No Longer Employed by Util & Many Mgt Personnel Changes Taken Place,Resulting in Effective Mgt
PNO-I-98-029, on 980707,licensee Began Orderly Shutdown,As Required by TS LCO 3.3.7.5,to Correct & Modify Inoperable SRV Acoustic Monitor.Licensee Issued Press Release.Region I Public Affairs Prepared to Respond to Media Inquires
LG-14-129, Special Report - Accident Monitoring Instrumentation Inoperability
LG-85-005, Forwards Reg Guide 1.97 Compliance Rept,Providing Description of Requirements & Method of Complying W/ Requirements for Each post-accident Variable Identified in Table 1 of Guide
LR-N09-0206, Special Report - North Plant Vent Radiation Monitoring System (RMS)
05000352/LER-2009-001, Regarding Neutron Flux Accident Monitoring Instrumentation Inoperable
LR-N08-0053, Submittal of Special Report - North Plant Vent Radiation Monitoring System (RMS)
LR-N08-0243, Special Report Update - North Plant Vent Radiation Monitoring System (RMS)
05000354/LER-2005-001-01, Special Report 05-001-01 Regarding the Cause of Failure and Channel Restoration
05000354/LER-2004-007, Regarding Technical Specification Noncompliance - Radiation Effluent Monitor on North Plant Vent
05000354/LER-2003-009, Regarding Technical Specification Noncompliance - Inoperable High Range Noble Gas Effluent Monitor on North Plant Vent
AECM-84-0536, Special Rept 84-038/0:on 841202,fuel Handling Area Ventilation Exhaust Accident Range Radiation Monitor Exceeded 72 H Limiting Condition for Operation.Caused by Failure of Normal Range Monitor Alarm Card.Card Replaced
U-601844, Submits Addl Info Re Proposed License Amend Due to Inoperable Position Indication for MSL Isolation Valve 1B21-FO22D,per 910515 Request for Amend to License NPF-62
PY-CEI-NRR-1946, Special Rept:On 950405,Unit Vent Gas Post Accident Radiation Monitoring Channel Was Declared Inoperable Based on Results of Testing Conducted in Accordance W/Surveillance Instruction SVI-D19-T5353
GO2-90-078, Application for Amend to License NPF-21,revising Tech Spec 3.3.7.5 to Allow Exception to Spec 3.0.4 During Periods When Accident Monitoring Instrumentation Channels Inoperable
LR-N25-0047, Special Report Pursuant to the Requirements of Hope Creek Technical Specification 3.3.7.5, Action 81, for the North Plant Plant Vent Radiation Monitor Inoperable for Greater than 72 Hours
PLA-2961, Forwards Rept Summarizing 1986 Approved Safety Evaluations, Per 10CFR50.59
05000353/LER-1990-020-02, :on 901119,primary Containment post-LOCA Radiation Monitoring Sys Declared Inoperable Due to Deficient Circuit Board in Three of Four Channels.Caused by Inadequate Design Review.Replacement Installed