Bob Fitzpatrick# QUERY93bf184ea67c66d3327d5fddecb4f8c7
Bob Fitzpatrick# QUERYa6e222de17bd13570b3f85f2655dd9dc
Bob Fitzpatrick# QUERY33abee59539648697eb65c5d20ea0f46
Bob Fitzpatrick# QUERYc66fd0c5afb4fd67f3d89c92eebf9011
Bob Fitzpatrick OR Bob Fitzpatrick
Bob Fitzpatrick# QUERY71da37ddecbfae83f71652e96754c687
Bob Fitzpatrick# QUERY497784cae468fc3a2387e75ffeae561a
Bob Fitzpatrick# QUERYaeebc0f29ff15518caa550e39669b270
Bob Fitzpatrick
Bob Fitzpatrick# QUERY720de46da583bc772512a1cdb83e8473
Bob Fitzpatrick# QUERY914c9e2d9d98666030e335fbc93d475d
NRC/NRR/DE/EENB false
Bob Fitzpatrick# QUERY8cad6707f89d09ca0eb30d9a25714df7
NRC/NRR/DE/EENB true
Bob Fitzpatrick# QUERY627f55e026df8d7331e99e2e3462ed81
NRC Headquarters
Bob Fitzpatrick# QUERYde076fd0735aa8b856faf204727da28d
05000247/LER-1982-027-03, /03L-0:on 820621,during Normal Operation,Boron Injection Tank Level Indicator Read Low.Caused by Solidification of Boric Acid in Instrument Pulse Line. Line Cleared & Instrument Returned to Normal Operation
05000247/LER-1982-032-01, /01T-0:on 820817,blowdown Outer Isolation Valve PCV 1215A Failed Closed Due to Failure of Solenoid Valve SOV 1315A.Caused by Open Circuit in Pilot Solenoid Valve SOV 1315A Coil.Coil Replaced
05000247/LER-1982-019-03, /03L-0:on 820517,auxiliary Boiler Feed Pump 23 Failed.Caused by Damaged Thrust Bearing Due to Equalizing Line Check Valve Hanging Up,Negating Positioning Control of Balancing Drum.Bearing Replaced & Check Valves Removed
05000247/LER-1982-031-99, /99X-0:on 820811,svc Water Leak in Containment Indicated by Increases in Containment Sump Collection Rate & Sodium Chloride Concentration.Caused by Under Deposit Corrosion Resulting in Pinhole Leaks
05000247/LER-1982-028-03, /03L-0:on 820720,operator Observed Low Air Flow Condition to R11/R12 Containment Gas & Particulate Monitors. Caused by Moisture on Electrical Leads.Source of Moisture Corrected & Motor Leads Dried & Reconnected
05000247/LER-1982-025-03, /03L-0:on 820530,steam Generator 21 Level Indicators Drifted Upscale.Caused by Foxboro Co Transmitter 417C Failure.Bistables Associated W/Reactor Protection Sys Placed in Trip Condition
05000247/LER-1982-030-03, /03L-0:on 820710,during Normal Operation,Bypass Valve 267A in Chemical & Vol Control Sys Found Leaking. Caused by Damaged Diaphragm.New Valve Bonnet Assembly & Diaphragm Installed